In this guide
Each new room in a house should have adequate ventilation for general health reasons. The type of room will determine how much ventilation is required.
When inserting a new internal wall care should be taken not to make any other matters, such as ventilation worse. If a new room is being created as a result of the addition of an internal wall then care should also be taken to ensure that the existing room is ventilated adequately.
The general rules for ventilating a room are:
Purge - this is achieved by opening the window. The opening should have a typical area of at least 1/20th of the floor area of the room served, unless it is a bathroom which can be any openable size.
Whole Building - this is also known as trickle ventilation which can be incorporated in to the head of the window framework, or by some other means. The area varies on the type of room:
- Bathroom – 4000mm²
- All other rooms – 8000mm²
Both of these forms of ventilation are normally required, however alternative approaches to ventilation may also be acceptable, subject to agreement with the Building Control Body.
Mechanical extract fans
Any new kitchen, utility room, bath/shower room or WC with no openable window should be provided with a mechanical extract fan to reduce condensation and remove smells. The necessary performance of these extract fans is normally measured in litres per second (l/s) as follows:
- Kitchen - 30l/s if placed over the hob and 60lt/s if place elsewhere.
- Utility room - 30l/s
- Bath/shower - 15l/s with a 15 minute overrun (after the light is switched out) if there is no openable window.
- WC - 6l/s with overrun.
Alternative rates may be applicable if the ventilation is running continuously.